The length of your snake.
Undefined. There is no maximum distance specified in the code.
Never be used on a fire alarm system.
Shall be permitted to be used for fire alarm purposes only by permission of the authority having jurisdiction.
Shall not be permitted to be used for fire alarm purposes unless approved by an electrical engineer qualified to test such cables.
Must be terminated by a certified cable technician certified by ANSI.
Within 10 feet of the floor.
Within 10 feet of the ceiling.
Within 7 feet of the floor.
Below all other wires.
Above all other wires.
In between cables used for telecommunication and power cables.
Under all other wires except communications wires.
Circuit Secondary Voltage Test
Testing for compliance with CP-01 standards when packaged as a complete assembly
Output Current and Power Test
Rated Output Heating Test
1 1/4 inch
12 inches / 5 feet
3 feet / 10 feet
18 inches / 10 feet
6 inches / 10 feet
Communications, signal, and control conductors.
Line voltage connections.
Class 1 connections.
None. A box is always required for a splice.
Flexible metal conduit
Rigid metal conduit
Any of the above
None of the above