# NFPA 13 - Les Installations

Approved & Edited by ProProfs Editorial Team
The editorial team at ProProfs Quizzes consists of a select group of subject experts, trivia writers, and quiz masters who have authored over 10,000 quizzes taken by more than 100 million users. This team includes our in-house seasoned quiz moderators and subject matter experts. Our editorial experts, spread across the world, are rigorously trained using our comprehensive guidelines to ensure that you receive the highest quality quizzes.
Learn about Our Editorial Process
| By ProjetSharp2013
P
ProjetSharp2013
Community Contributor
Quizzes Created: 4 | Total Attempts: 3,661
Questions: 77 | Attempts: 130

Settings

Toutes les questions de ce quizz ont été tirés du cours 311 244- du College montmorency

Questions and Answers
• 1.

### Quel est le débit d'une tête de gicleur ?

• A.

10 à 30 GPM

• B.

20 à 40 GPM

• C.

40 à 70 GPM

• D.

50 à 75 GPM

Correct Answer
B. 20 à 40 GPM
Explanation
The correct answer is 20 à 40 GPM. This range represents the flow rate of a nozzle head, which is the amount of water that the nozzle can deliver per minute. GPM stands for gallons per minute. This range indicates that the nozzle can deliver water at a flow rate between 20 and 40 gallons per minute.

Rate this question:

• 2.

### Cochez les tuyaux aériens verticaux :

• A.

Canalisations de distribution

• B.

Conduites transversales

• C.

Conduites d'alimentation

• D.

Colonne Montante

• E.

Remi-raccord

Correct Answer(s)
D. Colonne Montante
E. Remi-raccord
Explanation
The correct answer is "Colonne Montante" and "Remi-raccord". These are the two options that refer to vertical aerial pipes. "Colonne Montante" translates to "riser pipe" in English, which is a vertical pipe that carries water or other fluids from a lower level to a higher level in a building. "Remi-raccord" refers to a vertical pipe connection or joint. Therefore, both options are related to vertical aerial pipes.

Rate this question:

• 3.

### Quel doit être la température minimale pour un systeme sous eau ?

• A.

0 celsius

• B.

4 celsius

• C.

7 celsius

• D.

11 celsius

Correct Answer
B. 4 celsius
Explanation
The minimum temperature for a system underwater should be 4 degrees Celsius. This is because water freezes at 0 degrees Celsius, so any temperature below 0 degrees would cause the water to freeze and potentially damage the system. Therefore, the temperature should be kept above freezing point to ensure the system functions properly.

Rate this question:

• 4.

### Comment nomme t-on cela en anglais :

Correct Answer
straight pipe riser
pipe riser
Explanation
The given answer suggests that both "straight pipe riser" and "pipe riser" are the English terms used to describe the mentioned object.

Rate this question:

• 5.

### Un systeme antigel doit avoir un maximum de ______ têtes de gicleurs

• A.

5

• B.

10

• C.

15

• D.

20

Correct Answer
D. 20
Explanation
A systeme antigel doit avoir un maximum de 20 têtes de gicleurs.

Rate this question:

• 6.

### Le Volume max. du réseau du systeme antigel est de :

• A.

40 Gallon us

• B.

100 Gallon us

• C.

200 gallon us

Correct Answer
A. 40 Gallon us
Explanation
The maximum volume of the antifreeze system is 40 gallons.

Rate this question:

• 7.

### Dans un systeme antigel les 2 solutions utilisées sont : Mélange eau/glycerine pure Ou Glycol de propylene

• A.

True

• B.

False

Correct Answer
A. True
Explanation
The given statement is true. In an antifreeze system, two solutions are commonly used: a mixture of water and pure glycerine or propylene glycol. These solutions help prevent freezing and ensure that the system operates efficiently in low temperatures.

Rate this question:

• 8.

### Temps de fonctionnement maximal doit être de ______ secondes = Temps de déclenchement du dispositif + Temps de la soupape d’alarme + Temps de l’eau à atteindre le robinet de l’inspecteur

• A.

15

• B.

30

• C.

45

• D.

60

Correct Answer
D. 60
Explanation
The maximum operating time should be the sum of the triggering time of the device, the alarm valve time, and the time it takes for the water to reach the inspector's faucet. In this case, the correct answer is 60 seconds, which means that the maximum operating time should be 1 minute.

Rate this question:

• 9.

### Un systeme préaction doit avoir un maximum de ______ têtes de gicleur

• A.

400

• B.

700

• C.

1000

• D.

2000

Correct Answer
C. 1000
Explanation
A preaction system is a type of fire protection system that combines features of both a dry pipe system and a wet pipe system. It is designed to minimize the risk of accidental water discharge by requiring two independent events to occur before water is released. One of the key components of a preaction system is the sprinkler heads or nozzles. The question asks for the maximum number of sprinkler heads that a preaction system can have. The correct answer is 1000, indicating that a preaction system can accommodate up to 1000 sprinkler heads for effective fire protection.

Rate this question:

• 10.

### Quel doit être la pression de l'air dans un systeme préaction ?

• A.

4 lbs po2

• B.

7 lbs po2

• C.

14 lbs po2

• D.

21 lbs po2

Correct Answer
B. 7 lbs po2
Explanation
In a preaction system, the air pressure should be 7 lbs po2. This is the correct answer because a preaction system is a type of fire sprinkler system that requires a higher air pressure to prevent accidental discharge of water. By maintaining a pressure of 7 lbs po2 in the system, it ensures that the water will only be released when the fire detection system is activated, providing an additional layer of safety and preventing false alarms.

Rate this question:

• 11.

### Dans un systeme préaction, a partir de combien de têtes devons nous superviser l'étanchéité de la tuyauterie ?

• A.

10

• B.

20

• C.

30

• D.

40

Correct Answer
B. 20
Explanation
In a pre-action system, the leakage of the piping should be supervised from a minimum of 20 heads. This means that at least 20 sprinkler heads should be monitored for any leaks or faults in the piping system. This is important to ensure the effectiveness and reliability of the system in case of a fire.

Rate this question:

• 12.

### Le systeme FireCycle à la caractéristique d'etre capable de fermer le systeme automatiquement

• A.

True

• B.

False

Correct Answer
A. True
Explanation
The given statement is true because the FireCycle system has the capability to automatically shut down the system. This feature ensures that in case of a fire or any other emergency situation, the system can be quickly and safely turned off to prevent further damage or harm.

Rate this question:

• 13.

### Le systeme FireCycle Arrête l’écoulement aux têtes de ______ minutes après le rétablissement de la température ambiante à la température des détecteurs.

• A.

1 à 5 minutes

• B.

5 à 10 minutes

Correct Answer
A. 1 à 5 minutes
Explanation
The FireCycle system stops the flow at the heads within 1 to 5 minutes after the ambient temperature is restored to the temperature of the detectors.

Rate this question:

• 14.

### Le systeme FireCycle Se remet en fonction si la température atteint à nouveau la température de déclenchement des détecteurs

• A.

True

• B.

False

Correct Answer
A. True
Explanation
The statement is true because the FireCycle system will only reset and resume its function if the temperature once again reaches the triggering temperature of the detectors. This means that the system will continue to monitor and respond to temperature changes as long as it is necessary for fire detection and prevention.

Rate this question:

• 15.
• A.

OS&Y

• B.

WPIV

• C.

PIV

Correct Answer
A. OS&Y
• 16.

### Dans un systeme sous air, le ratio du principe différentiel est de :

• A.

4 pour 1

• B.

2 pour 1

• C.

6 pour 1

• D.

10 pour 1

Correct Answer
C. 6 pour 1
Explanation
In a pneumatic system, the ratio of the differential principle is 6 to 1. This means that for every 6 units of force applied, there will be 1 unit of force output. This ratio is important in understanding the amplification of force in pneumatic systems and how they can be used to generate powerful movements or actions.

Rate this question:

• 17.

### Dans une systeme sous air, il est recommandé d'ajouter dans la partie sous air, une pression de _______

• A.

5 à 10 lbs

• B.

10 à 15 lbs

• C.

15 à 20 lbs

Correct Answer
C. 15 à 20 lbs
Explanation
Dans un système sous air, il est recommandé d'ajouter une pression de 15 à 20 lbs dans la partie sous air. Cette pression supplémentaire permet de garantir un fonctionnement optimal du système et d'assurer une circulation adéquate de l'air. Une pression inférieure pourrait entraîner des problèmes de performance et une pression supérieure pourrait endommager le système. Par conséquent, une pression de 15 à 20 lbs est considérée comme idéale pour maintenir l'équilibre et assurer un bon fonctionnement.

Rate this question:

• 18.

### Dans un systeme sous ais : l'Essai à l’air hydrostatique à une pression de 40 lb/po2 (280 kPa) durant 24 heures, s’il y a une chute de pression supérieure à ______ lb/po2 la fuite doit être obstruée

• A.

1,5 lb po2

• B.

4,5 lb po2

• C.

7,5 lb po2

Correct Answer
A. 1,5 lb po2
Explanation
During the hydrostatic air test, if the pressure drops more than 1.5 lb/po2, it indicates that there is a leak and it needs to be blocked or sealed.

Rate this question:

• 19.

### La chambre à retardement à normalement une capacité de

• A.

1 gallon

• B.

2 gallon

• C.

5 gallon

• D.

10 gallon

Correct Answer
B. 2 gallon
Explanation
The correct answer is 2 gallon. A "chambre à retardement" is a French term that translates to "delay chamber" in English. It is commonly used in the context of engines and combustion processes. The capacity of a delay chamber is typically measured in gallons and refers to the volume of fuel and air mixture that can be stored before it is ignited. In this case, the delay chamber has a capacity of 2 gallons, meaning it can hold 2 gallons of the fuel and air mixture before ignition.

Rate this question:

• 20.

### Un surpresseur a généralement une capacité de ______ gpm

• A.

1

• B.

7

• C.

3

• D.

11

Correct Answer
C. 3
Explanation
A surpresseur is a device used to increase the pressure of a fluid. The given question is asking for the typical capacity of a surpresseur, which is measured in gallons per minute (gpm). Among the options provided, the correct answer is 3 gpm.

Rate this question:

• 21.

### Un surpresseur peut donner une pression de :

• A.

30 lbs

• B.

50 lbs

• C.

74 lbs

• D.

100 lbs

Correct Answer
B. 50 lbs
Explanation
A surpresseur is a device used to increase the pressure of a fluid. In this question, the options provided are different pressure values that a surpresseur can deliver. The correct answer is "50 lbs", which means that a surpresseur can provide a pressure of 50 pounds per square inch.

Rate this question:

• 22.

### Dans un systeme sous air, les raccords pompier sont placé :

• A.

En AVAL de la soupape d’alarme sur les systèmes

• B.

En AMONT de la soupape d’alarme sur les systèmes

Correct Answer
B. En AMONT de la soupape d’alarme sur les systèmes
Explanation
Dans un système sous air, les raccords pompier sont placés en amont de la soupape d'alarme. Cela signifie qu'ils sont situés avant la soupape d'alarme dans le flux d'air. Cette disposition permet de garantir que les raccords pompier sont accessibles et utilisables en cas d'urgence, sans que la soupape d'alarme ne bloque leur accès.

Rate this question:

• 23.

### Dans un systeme sous eau, les raccords pompier sont placé :

• A.

En AVAL de la soupape d’alarme sur les systèmes

• B.

En AMONT de la soupape d’alarme sur les systèmes

Correct Answer
A. En AVAL de la soupape d’alarme sur les systèmes
Explanation
Dans un système sous eau, les raccords pompier sont placés en aval de la soupape d'alarme sur les systèmes. Cela signifie qu'ils sont situés après la soupape d'alarme dans le flux d'eau. Cela permet de s'assurer que l'eau passe d'abord par la soupape d'alarme avant d'atteindre les raccords pompier, ce qui permet de détecter toute augmentation de pression ou de débit anormale et d'activer l'alarme en conséquence. Placer les raccords pompier en amont de la soupape d'alarme pourrait compromettre son bon fonctionnement et sa capacité à détecter les problèmes.

Rate this question:

• 24.

### Un compresseur doit produire la pression normale dans le systeme en moins de :

• A.

10 minutes

• B.

5 minutes

• C.

30 minutes

Correct Answer
C. 30 minutes
Explanation
A compressor needs to reach the normal pressure in the system within 30 minutes. This indicates that the compressor should be able to efficiently increase the pressure to the desired level within this time frame. If it takes longer than 30 minutes, it may indicate a problem with the compressor or the system itself, leading to inefficiency or potential malfunctions.

Rate this question:

• 25.

### Distance maximum entre les raccords pompiers et le sol

• A.

X

• B.

Y

Correct Answer
A. X
Explanation
The question is asking for the maximum distance between the fire hose connections and the ground. The correct answer is "x," but without further context, it is unclear what "x" represents. It could be a specific measurement or a variable that needs to be defined. Without more information, it is not possible to provide a clear explanation for the correct answer.

Rate this question:

• 26.

### Distance maximum entre les raccords pompiers et un poteau d’incendie

• A.

X

• B.

Y

Correct Answer
A. X
Explanation
The question is asking for the maximum distance between fire hydrant connections and a fire hydrant. However, the options provided (x and y) do not provide any context or specific values. Therefore, without additional information, it is not possible to determine a specific distance or provide an explanation.

Rate this question:

• 27.

### Espace libre devant et autour des raccords pompiers

• A.

X

• B.

Y

Correct Answer
A. X
• 28.

### Quel est ce type de systeme d'autoprotection ?

Correct Answer
Microdrop
Explanation
Utiliser par exemple pour un transformateur d'hydroquebec.... haute pression et particules deau tres petites

Rate this question:

• 29.

### Quel doit être l'espacement minimale entre les têtes de gicleurs ?

• A.

6 à 12 pieds

• B.

4 à 8 pieds

• C.

9 à 16 pieds

Correct Answer
A. 6 à 12 pieds
Explanation
The minimum spacing between sprinkler heads should be 6 to 12 feet. This means that the distance between each sprinkler head should be at least 6 feet but no more than 12 feet. This spacing allows for adequate coverage of the area being irrigated while avoiding excessive overlap or gaps in water distribution.

Rate this question:

• 30.

### Support et Étrier Les supports et les points d’encrages doivent soutenir une charge de _____ x le poids du tuyau plein d’eau + _____ lb

• A.

3 fois + 252 livres

• B.

4 fois + 252 livres

• C.

5 fois + 252 livres

• D.

6 fois + 252 livres

Correct Answer
C. 5 fois + 252 livres
Explanation
The supports and anchor points need to support a load that is 5 times the weight of the pipe filled with water plus an additional 252 pounds.

Rate this question:

• 31.

### Quel est la distance minimale qu'un gicleur peut avoir d'un mur ?

• A.

2 pouces

• B.

4 pouces

• C.

6 pouces

• D.

8 pouces

Correct Answer
B. 4 pouces
Explanation
The correct answer is 4 pouces. This means that the minimum distance a sprinkler can have from a wall is 4 inches.

Rate this question:

• 32.

### Quel serait la distance minimale entre les gicleurs ?

• A.

4 pieds

• B.

6 pieds

• C.

10 pieds

• D.

12 pieds

Correct Answer
B. 6 pieds
Explanation
The minimum distance between the sprinklers would be 6 feet.

Rate this question:

• 33.

### Un gicleur de couloir ou sans couleur propre a une température de déclenchement de :

• A.

40 à 62 celsius

• B.

55 à 77 celsius

• C.

79 à 107 celsius

• D.

121 à 149 celsius

Correct Answer
B. 55 à 77 celsius
Explanation
The correct answer is 55 à 77 celsius. This is the temperature range at which a corridor or colorless sprinkler nozzle will be triggered.

Rate this question:

• 34.

### Selon la NFPA 13, quel est le pourcentage de déces qui se produisent dans les batiments résidentiels ?

• A.

39%

• B.

59%

• C.

69%

• D.

89%

Correct Answer
D. 89%
Explanation
According to NFPA 13, 89% of deaths occur in residential buildings.

Rate this question:

• 35.

### Dans les 5 phases du FEU, la phase ( Production de flammes ) est :

• A.

Phase2

• B.

Phase3

• C.

Phase4

Correct Answer
B. Phase3
Explanation
The correct answer is phase3. In the 5 phases of a fire, the phase of "Production de flammes" refers to the stage where flames are actively being produced. This phase typically occurs after the initial ignition and the fire has gained enough heat and fuel to sustain a flame. It is a critical stage where the fire can rapidly spread and intensify.

Rate this question:

• 36.

### Dans les 5 phases du FEU, la phase ( Production de chaleur ) est :

• A.

Phase2

• B.

Phase3

• C.

Phase4

Correct Answer
C. Phase4
Explanation
Dans les 5 phases du FEU, la phase "Production de chaleur" est la phase 4.

Rate this question:

• 37.

### Détectent un phénomène du feu à un point direct de sont environnement de localisation

• A.

Détecteurs ponctuels

• B.

Détecteurs linéaires

• C.

Détecteurs multiponctuels

Correct Answer
A. Détecteurs ponctuels
Explanation
The given correct answer is "Détecteurs ponctuels". This is because the phrase "Détectent un phénomène du feu à un point direct de sont environnement de localisation" translates to "Detect a fire phenomenon at a specific point in its location environment." This suggests that the detectors being referred to are able to detect fires at a specific point or location, which aligns with the concept of "détecteurs ponctuels" or point detectors.

Rate this question:

• 38.

### Détectent les variations de critères d’analyse d’activation des détecteurs, le long d’une ligne continue, chacun des points de cette ligne constituant un des éléments du capteur de détection

• A.

Détecteurs ponctuels

• B.

Détecteurs linéaires

• C.

Détecteurs multiponctuels

Correct Answer
B. Détecteurs linéaires
Explanation
The correct answer is "Détecteurs linéaires". This is because the given statement describes the detection of variations in activation analysis criteria along a continuous line, with each point on this line being one of the elements of the detection sensor. This suggests that the sensors used for detection are linear in nature, hence the term "Détecteurs linéaires" is the most appropriate choice.

Rate this question:

• 39.

### Détectent un phénomène du feu à un certain nombre de points déterminés (Détecteur à aspiration)

• A.

Détecteurs linéaires

• B.

Détecteurs multiponctuels

• C.

Détecteurs ponctuels

Correct Answer
B. Détecteurs multiponctuels
Explanation
The correct answer is "Détecteurs multiponctuels". This answer suggests that the detectors are able to detect a fire phenomenon at multiple specific points. This implies that the detectors are designed to identify fires in different areas or zones, allowing for more accurate and targeted fire detection and response.

Rate this question:

• 40.

### Tous les avertisseurs manuels actionnés par clés dans un réseau avertisseur d’incendie doivent présenter un fonctionnement identique et pouvoir être déclenchés par une clé de même modèle

• A.

True

• B.

False

Correct Answer
A. True
Explanation
All manually operated key-operated warning devices in a fire alarm system must have the same operation and be able to be triggered by a key of the same model.

Rate this question:

• 41.

### Dans un système à une étape, codé, Le code est donné à au moins _________ reprises et suivie de l’alarme générales

• A.

3

• B.

4

• C.

5

Correct Answer
A. 3
Explanation
Dans un système à une étape, le code est donné au moins 3 fois et suivi de l'alarme générale.

Rate this question:

• 42.

### Installation des postes manuels •Devrait être de couleur rouge « Alarme incendie » et installé sur un mur de couleur contrastante du rouge Installation du poste manuel doit être à ______.  de distance de l’issue

• A.

48 po

• B.

60 po

• C.

72 po

Correct Answer
B. 60 po
Explanation
The correct answer is 60 po. The installation of the manual post should be 60 inches away from the exit.

Rate this question:

• 43.

### Ajout de postes manuels si la distance horizontalement dépasse une distance de _______ du poste manuel le plus rapproché.

• A.

100 pieds

• B.

150 pieds

• C.

200 pieds

Correct Answer
C. 200 pieds
Explanation
If the horizontal distance exceeds 200 feet from the closest manual post, additional manual posts should be added.

Rate this question:

• 44.

### Multi-portes • Les issues à multi-portes dépassant plus de _______ de largeur doivent-être munies de postes manuels de chaque côté et ce à 60 po. (1,52m) de l’issue

• A.

20 pieds

• B.

30 pieds

• C.

40 pieds

• D.

60 pieds

Correct Answer
C. 40 pieds
• 45.

### Fonctionnement thermovélocimétrique : Lorsqu'il y a une augmentation de température au taux de ______ par minute (feu violent), ceci provoque une dilatation de l'air dans l'hémisphère plus rapidement qu'il ne peut s'échapper par l'évent (calibré à cet effet). L'excès de pression exerce alors une poussé sur le diaphragme qui à son tour se déforme pour activer la fermeture du contact "A" et ainsi fermer le circuit électrique pour donner l'alarme.

• A.

9,4 degrés

• B.

12,4 degrés

• C.

7,1 degrés

• D.

16,16 degrés

Correct Answer
A. 9,4 degrés
Explanation
When there is an increase in temperature at a rate of 9.4 degrees per minute (violent fire), it causes air to expand in the hemisphere faster than it can escape through the vent (calibrated for this purpose). The excess pressure then pushes on the diaphragm, which in turn deforms to activate the closure of contact "A" and thus close the electrical circuit to sound the alarm.

Rate this question:

• 46.

### Conditions qui influence le déclenchement d’un détecteur de fumée •La vélocité de l’air •Le niveau d’altitude •Le taux d’humidité •Le degré de température •La couleur de la fumée

• A.

True

• B.

False

Correct Answer
A. True
Explanation
The conditions that influence the triggering of a smoke detector include the velocity of the air, the level of altitude, the humidity level, the degree of temperature, and the color of the smoke. These factors can affect the sensitivity and effectiveness of the smoke detector in detecting smoke particles in the air. Therefore, the statement "True" indicates that the given conditions can indeed influence the activation of a smoke detector.

Rate this question:

• 47.

### L'américium peut être dangereux s'il est absorbé sous forme soluble dans le corps. Toutefois, l’ingestion d'américium n'entraînera pas l'absorption d'une quantité importante ________. Le dioxyde étant insoluble, la dose de rayonnement pour le système digestif est insignifiante.

• A.

Americium 231

• B.

Américium 131

• C.

Américium 241

Correct Answer
C. Américium 241
Explanation
Américium 241 is the correct answer because the passage states that the ingestion of americium will not result in significant absorption if it is in the form of insoluble dioxide. Since américium 241 is mentioned in the passage and the other options are not, it can be inferred that américium 241 is the specific form of americium being referred to in the passage.

Rate this question:

• 48.

### Rayon infrarouge

• A.

< 0,4 μm

• B.

0,4 μm à 0,75 μm

• C.

> 0,75 μm

Correct Answer
C. > 0,75 μm
Explanation
The given answer "> 0,75 μm" suggests that the wavelength of infrared rayon is greater than 0,75 μm. Infrared rays have longer wavelengths than visible light, and wavelengths greater than 0,75 μm fall within the infrared spectrum. Therefore, this answer indicates that the given rayon is emitting infrared radiation with a wavelength greater than 0,75 μm.

Rate this question:

• 49.

### Rayon ultraviolet

• A.

< 0,4 μm

• B.

0,4 μm à 0,75 μm

• C.

> 0,75 μm

Correct Answer
A. < 0,4 μm
Explanation
The correct answer is "< 0,4 μm" because rayon ultraviolet refers to the range of wavelengths that fall below 0,4 μm. This range of wavelengths is shorter than both the 0,4 μm to 0,75 μm range and the range above 0,75 μm.

Rate this question:

• 50.

### Rayons visibles

• A.

0,4 μm à 0,75 μm

• B.

0,9 μm à 0,95 μm

• C.

1,4 μm à 3,75 μm

Correct Answer
A. 0,4 μm à 0,75 μm
Explanation
The correct answer is 0.4 μm to 0.75 μm. This range corresponds to the wavelengths of visible light. Visible light is the portion of the electromagnetic spectrum that can be detected by the human eye. It includes colors ranging from violet (shorter wavelength) to red (longer wavelength). This range is commonly used in various applications such as photography, microscopy, and optical communication.

Rate this question:

Quiz Review Timeline +

Our quizzes are rigorously reviewed, monitored and continuously updated by our expert board to maintain accuracy, relevance, and timeliness.

• Current Version
• Mar 15, 2023
Quiz Edited by
ProProfs Editorial Team
• Jul 14, 2013
Quiz Created by
ProjetSharp2013
Back to top
Advertisement
×

Wait!
Here's an interesting quiz for you.